- TECHNICAL CENTER
- Compliance Surveys
- Reference Charts
- Refererence Pages
- Site Map
- CUSTOMER SERVICE
- Contact Us
- How to Order
- Quality Guarantee
- Price Guarantee
- Request A Quote
- Request A Sample
- Distributor Sign Up
Safety, Storage & Security Cabinet Regulations
|OSHA 29 CFR 1910.106(e)(2)(ii)(b): |
Incidental storage or use of flammable and combustible liquids.
(b) The quantity of liquid that may be located outside of an inside storage room or storage cabinet in a building or in any one fire area of a building shall not exceed: (1) 25 gallons of Class IA liquids in containers (2) 120 gallons of Class IB, IC, II or III liquids in containers (3) 660 gallons of Class IB, IC, II or III liquids in a single portable tank
OSHA 29 CFR 1910.106(d)(3)(i&ii):
Design, construction, and capacity of storage cabinets - (i) Maximum capacity. Not more than 60 gallons of Class l or Class ll liquids, nor more than 120 gallons of Class lll liquids may be stored in a storage cabinet.
(ii) Fire resistance. Storage cabinets shall be designed and constructed to limit the internal temperature to not more than 325ºF. when subjected to a 10-minute fire test using the standard time-temperature curve as set forth in Standard Methods of Fire Tests of Building Construction and Materials, NFPA 251-1969.
Related Products - That Can Help You Comply
Related Documents & Links